Valley GENERAC Generator Dealer
GENERAC SERVICE - PARTS - INSTALLATION
Generators restore normal
electricity supply to your home in the event that the electricity
supply is interrupted from the utility company or the result of severe
weather. These generators are fueled by
Natural Gas or Propane to give you continuous
operation without having to worry with refilling a fuel tank.
generators will automatically supply power to your home or office even
while your away.
| Generac Preventive Maintenance & Warranty Dealer
recommends having your new
generator serviced after the break-in period from 8 to 20 hours of use
at 1 year. This
includes changing the oil and filter, checking and adjusting the valve
clearance, clean spart plugs, voltage adjustment, frequency adjustment
and a overall
inspection. Then have yearly preventive maintenance done not to
exceed 200 hours between oil changes. We provide
maintenance and factory warranty
service for Generac Air-Cooled
home standby generators from 7KW to
20KW and liquid cooled gaseous units to 150KW. The
brands are made and warranted by Generac.: Lowes Centurian, Sears,
costs for air-cooled generators 7KW-22KW - New or clean spark plugs as needed, new
oil (Mobile 1), new
oil filter change, New air filter change as needed, remove valve covers and adjust valves,
clean unit, visual inspection, governor adjustment, check air filter, choke, battery cold cranking amp check
and run test...............................$195.00****************Same price since 2009
Generac recommends a new battery every 2-3 years. Usually 3-4 years
it fine as long as Cold Cranking Amps is above 440 CCA.
provide maintenance and repairs on Generac liquid-cooled
natural gas and
propane generators up to 150 KW. Contact us for pricing.
Take a look at the
Generac full line of generators Here.
Click Here to see pictures of recent installs.
The following is my Preventive Maintenance Checklist for Air-Cooled Generators:
Clean inside and out
Wipe protective coating on rubber bellows and
Change oil (5W-30 Mobile 1)
New Generac Oil filter
Update firmware on EVO panels
Check and (or) replace Air Cleaner
Clean and (or) replace Spark Plugs: and gap.
Check Voltage (approx. 240 volts).
Check Frequency 60 HZ.
Check automatic operation
Check and write down run time hours.
Check and write down CCA on battery � if below
440 CCA then replace battery.
Spray terminal protector on battery.
Adjust valves on generators that run rough or
break-in Maintenance is being done.
Check fuel pressure (5-7� W.C. for NG and 11-14�
W.C. for LP)
Fuel line inspection
Check choke operation.
Check to make sure Circuit Breaker is ON.
Check to make sure generator is set to AUTO
Reset Maintenance (yellow light)
Make sure both plug wires are connected.
Check battery connections. Tighten and spray
Install maintenance tag. Record what was done on tag: new oil, new oil filter, air filter, new
plugs, CCA of battery or new battery, hours, date.
Re-check oil level and tighten oil Cap
Additional items for Liquid-Cooled gernartors 22 KW - 150 KW